How can we help you?
All the JL-240 series Nema 7 Pin twist lock photocell receptacle were designed for the Street LED luminaires those intended to have an ANSI C136.10-2006 receptacle to fit a Twist-Lock photocontrol. This series conform newly published ANSI C136.41-2013 to allow a LED lamp multi-controlled through the Photocell Receptacle.
This JL-240 ANSI C136.41 Photocell Socket offers 2 or 4 gold-plated low voltage pads on the top surface to fit photocontrol has ANSI C136.41 conforming spring contacts, and offers male quick connectors at rear back for signal connection.
This series also offers 360 degree rotation limiting feature to conform ANSI C136.10 requirements.
Both JL-240X and JL-240Y have been recognized, and JL-200Z14 has been listed by UL to applicable US and Canadian safety standards, under their file E188110, Vol.1 & Vol.2.
ANSI C 136.41 Nema 7 Pin Twist Lock Photocell Receptacle
-ANSI C136.41-2013 to allow a LED lamp multi-controlled through the
-Offers 2 or 4 gold-plated low voltage pads on the top
surface to fit photocontrol has ANSI C136.41
conforming spring contacts,
-Offers male quick connectors at rear back for signal
-Listed by UL to applicable US and Canadian safety standards,
under their file E188110, Vol.1 & Vol.2.
Nema 7 Pin Photocell Receptacle Display
|Applicable Volt Range||0~480VAC|
|Power Loading||AWG#14: 15Amp max. / AWG#16: 10Amp max.|
|Optional Signal Loading||AWG#18: 30VDC, 0.25Amp max.|
|Ambient Temperature||-40℃ ~ +70℃|
|Overall Dimensions (mm)||65Dia.x 40||65Dia.x 67|
|Accessory||Rear Cover||● R option||●||● R option|
|Wall Mount Bracket||-||-|
|Leads||6” Min. (See Ordering Information)|
Disconnect power; wire the PhotoControl Receptacle according to the diagram below. An arrow indicating NORTH on the top of the Dusk to Dawn Photocell Sensor Receptacle is used to assist correct direction. Push the Photocontrol on and turn it clockwise to lock into the Photocell Switch Receptacle.
Adjust the receptacle position if necessary.
JL-240Y series Dusk to Dawn Photcontrol Socket supports tool-free rotation.
JL-240Z series Day Night Street Light PhotoController Receptacle supports Wall-mount and rotation.
It is normal for the SWITCH to take several minutes to turn off when first installed.
To test “turn on” during daytime, cover its eye with sliding the metal strip mounted.
Do not cover with finger because light traveling through fingers may be great enough to keep the switch open.
Test will take approximately 2 minutes.