JL-101 MINITYPE PHOTOELECTRIC SWITCH
The photoelectric switch JL-101 is applicable to control the street lighting, passage lighting and doorway lighting automatically in accordance with the ambient lighting level.
*JL-101A **09 ***/ L N
*: Model Number;
**: Lead Length (in inches);
***: Other Options:
L = Couple metal lock-nuts (Null = One metal lock-nut offered);
N = Neoprene O-ring gasket for outdoor use. (Null = One gasket offered)
-20℃ ~ +70℃
Brass made, ID 10mm
34(L) x 12.5(W) x 20(H)mm, Nipple Height 16mm
6” or Customer request (AWG#20)
4.Installation & Operational Instructions
Disconnect power, remove junction box cover, place the SWITCH in knockout hole and fasten with locknut.
Wire according to the diagram in right hand.
Do not install the switch with the Photocell facing artificial or reflected light. This will cause the unit to cycle on and off at night.
It is normal for the SWITCH to take several minutes to turn off when first installed.
To test “turn on” during daytime, cover its eye with sliding the metal strip mounted.
Do not cover with finger because light traveling through fingers may be great enough to keep the switch open.
Test will take approximately 2 minutes.
Shanghai Long-join Intelligent Technology Inc.
Add:2 floor 8 building Donglin Technology Park,No.129 Hulan west road,Baoshan District Shanghai China. Postalcode 200443